Rack transmission towers brand NE 95-20
- Customer pickup,
- In detail
- Country of manufactureBelarus
|Project documentation||Product brand||Sizes, mm|
|Series B 3.407.1-2.01||CB 110-35
POWER LINE 00.10-10SB
Racks the reinforced concrete power lines of 0,38 kV and from 6 to 10 kV which are previously strained for support inclusive intended for application at a settlement temperature of external air (average air temperature of the coldest five-day week of the area of construction) to minus 55 °C inclusive, seismicity to 7 points inclusive.
Support of the power line are applied at construction, reconstruction and capital repairs of high-voltage power lines.
Racks designate brands according to requirements of GOST 23 09. The brand consists of the alphanumeric groups divided by hyphens.
The first group contains rack designation (SV — the rack vibrated) and its length in decimeters.
Give the bearing ability of a rack in the second group. characterized by the size of the settlement bending moment in kN of m rounded to an integer, and a class of the strained fittings.
Include the additional characteristics reflecting special conditions of application of racks, type of protection of racks against corrosion, the reinforcing options designated by the Arab figures and capital letters in the third group.
Identification numbers (brands) of a support of the power line
Rack 9500 mm long with the settlement bending moment equal to 19.6 kN of m.
CB 95-3c-A * are resistant differ from SV 95-3c-A racks: face plates are not established; in a small end face of a support the probe is installed; the grounding conductors are welded on releases of the strained core. Racks are carried out on the basis of a series B 3.407.1-2.01 of the issue 1. The plastering of a komlevy part is not made. On production coordination of the customer on the specified changes is required.